# Heat transfer coefficient

The heat transfer coefficient, in thermodynamics and in mechanical and chemical engineering, is used in calculating the heat transfer, typically by convection or phase change between a fluid and a solid:

:$Delta Q=h cdot A cdot Delta T cdot Delta t$where:"ΔQ" = heat input or heat lost, J:"h" = heat transfer coefficient, W/(m2K):"A" = heat transfer surface area, m2:$Delta T$ = difference in temperature between the solid surface and surrounding fluid area, K:$Delta t$ = time period, s

From the above equation, the heat transfer coefficient is the proportionality coefficient between the heat flux, "Q"/("AΔt"), and the thermodynamic driving force for the flow of heat (i.e., the temperature difference, "ΔT").

The heat transfer coefficient has SI units in watts per meter squared-kelvin (W/(m2K)). Heat transfer coefficient can be thought of as an inverse of thermal resistance.

There are numerous methods for calculating the heat transfer coefficient in different heat transfer modes, different fluids, flow regimes, and under different thermohydraulic conditions. Often it can be estimated by dividing the thermal conductivity of the convection fluid by a length scale. The heat transfer coefficient is often calculated from the Nusselt number (a dimensionless number).

Dittus–Boelter correlation (forced convection)

A common and particularly simple correlation useful for many applications is the Dittus–Boelter heat transfer correlation for fluids in turbulent flow. This correlation is applicable when forced convection is the only mode of heat transfer; i.e., there is no boiling, condensation, significant radiation, etc. The accuracy of this correlation is anticipated to be +/-15%.

For a liquid flowing in a straight circular pipe with a Reynolds number between 10 000 and 120 000 (in the turbulent pipe flow range), when the liquid's Prandtl number is between 0.7 and 120, for a location far from the pipe entrance (more than 10 pipe diameters; more than 50 diameters according to many authors [S.S. Kutateladze and V.M. Borishanskii, "A Concise Encyclopedia of Heat Transfer", Pergamon Press, 1966.] ) or other flow disturbances, and when the pipe surface is hydraulically smooth, the heat transfer coefficient between the bulk of the fluid and the pipe surface can be expressed as:

:$h=$k_w}over{D_HNuwhere:$k_w$ = thermal conductivity of water:$D_H$ = Hydraulic diameter:"Nu" = Nusselt number: = $\left\{0.023\right\} cdot Re^\left\{0.8\right\} cdot Pr^\left\{n\right\}$ => Dittus-Boelter correlation:"Pr" = Prandtl number = $\left\{C_p cdot mu\right\}over\left\{k_w\right\}$:"Re" = Reynolds number = $\left\{dot m cdot D_H\right\}over\left\{mu cdot A \right\}$:$dot m$ = mass flow rate:"μ" = fluid viscosity:"C"p = heat capacity at constant pressure:"A" = cross-sectional area of flow:"n" = 0.4 for heating (wall hotter than the bulk fluid) and 0.3 for cooling (wall cooler than the bulk fluid) [F.Kreith (editor), "The CRC Handbook of Thermal Engineering", CRC Press, 2000.] .

The fluid properties necessary for the application of this equation are evaluated at the bulk temperature thus avoiding iterations.

Thom correlation

There exist simple fluid-specific correlations for heat transfer coefficient in boiling. The Thom correlation is for flow boiling of water (subcooled or saturated at pressures up to about 20 MPa) under conditions where the nucleate boiling contribution predominates over forced convection. This correlation is useful for rough estimation of expected temperature difference given the heat flux: [W.Rohsenow, J.Hartnet, Y.Cho, "Handbook of Heat Transfer", 3rd edition, McGraw-Hill, 1998.]

$Delta T_\left\{sat\right\} = 22.5 cdot \left\{q\right\}^\left\{0.5\right\} exp \left(-P/8.7\right)$

where::$Delta T_\left\{sat\right\}$ is the wall temperature elevation above the saturation temperature, K:q is the heat flux, MW/m2:P is the pressure of water, MPa

Note that this empirical correlation is specific to the units given.

Heat transfer coefficient of pipe wall

The resistance to the flow of heat by the material of pipe wall can be expressed as a "heat transfer coefficient of the pipe wall". However, one needs to select if the heat flux is based on the pipe inner or the outer diameter.

Selecting to base the heat flux on the pipe inner diameter, and assuming that the pipe wall thickness is small in comparison with the pipe inner diameter, then the heat transfer coefficient for the pipe wall can be calculated as if the wall were not curved:

:$h_\left\{wall\right\} = \left\{k over t\right\}$

where k is the effective thermal conductivity of the wall material and t is the wall thickness.

If the above assumption does not hold, then the wall heat transfer coefficient can be calculated using the following expression:

:$h_\left\{wall\right\} = \left\{2k over \left\{d_iln\left(d_o/d_i\right)$

where di and do are the inner and outer diameters of the pipe, respectively.

The thermal conductivity of the tube material usually depends on temperature; the mean thermal conductivity is often used.

Combining heat transfer coefficients

For two or more heat transfer processes acting in parallel, heat transfer coefficients simply add:

:$h = h_1 + h_2 + dots$

For two or more heat transfer processes connected in series, heat transfer coefficients add inversely. This means that the overall heat transfer coefficient is a harmonic mean of the partial heat transfer coefficients:

:$\left\{1over h\right\} = \left\{1over h_1\right\} + \left\{1over h_2\right\} + dots$

For example, consider a pipe with a fluid flowing inside. The rate of heat transfer between the bulk of the fluid inside the pipe and the pipe external surface is:

:$Q=left\left( \left\{1over$1 over h}+{t over k} ight) cdot A cdot Delta Twhere:"Q" = heat transfer rate (W):"h" = heat transfer coefficient (W/(m2.K)):"t" = wall thickness (m):"k" = wall thermal conductivity (W/m.K):"A" = area (m2):$Delta T$ = difference in temperature.

Overall heat transfer coefficient

The overall heat transfer coefficient, U, is the reciprocal of the overall thermal resistance across a heat exchanger. It is used to determine the total heat transfer between the two streams in the heat exchanger by the following relationship:

:$Q = U cdot A cdot Delta T$

where:"Q" = heat transfer rate (W):"U" = overall heat transfer coefficient (W/(m2.K)):"A" = area (m2):"ΔT" = log mean temperature difference (K)

The overall heat transfer coefficient takes into account the individual heat transfer coefficients of each stream and the resistance of the pipe material.

:$frac \left\{1\right\} \left\{UA\right\} = Sigma frac\left\{1\right\} \left\{hA\right\} + Sigma R$

where:R = Resistance(s) to heat flow in pipe wall (K/W):Other parameters are as above. [Coulson and Richardson, "Chemical Engineering", Volume 1,Elsevier, 2000]

The heat transfer coefficient is the heat transferred per unit area per Kelvin. Thus "Area" is included in the equation as it represents the area over which the transfer of heat takes place. The areas for each flow will be different as they represent the contact area for each fluid side.

The "thermal resistance" due to the pipe wall is calculated by the following relationship:

R=x/k.A

where:x = The wall thickness (m):k = the thermal conductivity of the material (W/mk):A = The total area of the heat exchanger (m2)

This represents the heat transfer by conduction in the pipe.

The "thermal conductivity" is a characteristic of the particular material. Values of thermal conductivities for various materials are listed in the list of thermal conductivities.

As mentioned earlier in the article the "convection heat transfer coefficient" for each stream depends on the type of fluid, flow properties and temperature properties.

Some typical heat transfer coefficients include:

:- Air - h = 10 to 100 W/m2K:- Water - h = 500 to 10 000 W/m2K

Thermal resistance due to fouling deposits

Surface coatings can build on heat transfer surfaces during heat exchanger operation due to fouling. These add extra thermal resistance to the wall and may noticeably decrease the overall heat transfer coefficient and thus performance. (Fouling can also cause other problems.)

The additional thermal resistance due to fouling can be found by comparing the overall heat transfer coefficient determined from laboratory readings with calculations based on theoretical correlations. They can also be evaluated from the development of the overall heat transfer coefficient with time (assuming the heat exchanger operates under otherwise identical conditions). This is commonly applied in practice, e.g. [Turner C.W.; Klimas S.J.; Bbrideau M.G., "Thermal resistance of steam-generator tube deposits under single-phase forced convection and flow-boiling heat transfer", Canadian Journal of Chemical Engineering, 2000, vol. 78, No 1, pp. 53-60] . The following relationship is often used:

$frac\left\{1\right\}\left\{U_\left\{exp$ = $frac\left\{1\right\}\left\{U_\left\{pre+R_f$

where::$U_\left\{exp\right\}$ = overall heat transfer coefficient based on experimental data for the heat exchanger in the "fouled" state, $frac\left\{W\right\}\left\{m^2K\right\}$:$U_\left\{pre\right\}$ = overall heat transfer coefficient based on calculated or measured ("clean heat exchanger") data, $frac\left\{W\right\}\left\{m^2K\right\}$:$R_f$ = thermal resistance due to fouling, $frac\left\{m^2K\right\}\left\{W\right\}$

References

ee also

* Thermal conductivity
* Heat
* Heat pump
* Thermal-hydraulics
* Churchill-Bernstein Equation

* [http://www.cheresources.com/uexchangers.shtml Overall Heat Transfer Coefficients]
* [http://www.cheresources.com/convection.shtml Correlations for Convective Heat Transfer]
* [http://www.hrs-spiratube.com/en/resources/heat_transfer_fundamentals_01_05.aspx Heat Transfer fundamentals]

Wikimedia Foundation. 2010.

### Look at other dictionaries:

• heat transfer coefficient — šilumos perdavos koeficientas statusas T sritis Standartizacija ir metrologija apibrėžtis Dydis, skaitine verte lygus šilumos kiekiui, kurį vienetinio ploto paviršius per vienetinį laiko tarpą perduoda aplinkai, kai paviršiaus ir aplinkos… …   Penkiakalbis aiškinamasis metrologijos terminų žodynas

• heat transfer coefficient — šilumos pernašos koeficientas statusas T sritis fizika atitikmenys: angl. heat transfer coefficient vok. Wärmeübertragungskoeffizient, m rus. коэффициент теплоотдачи, m pranc. coefficient de transfert de chaleur, m …   Fizikos terminų žodynas

• heat transfer coefficient — šilumos atidavimo koeficientas statusas T sritis Energetika apibrėžtis Dydis, apibūdinantis šilumos mainų tarp paviršiaus ir takiosios medžiagos intensyvumą ir parodantis šilumos kiekį, atiduotą nuo paviršiaus ploto vieneto per laiko vienetą,… …   Aiškinamasis šiluminės ir branduolinės technikos terminų žodynas

• heat transfer coefficient — Смотри коэффициент теплопередачи …   Энциклопедический словарь по металлургии

• heat transfer coefficient — Смотри коэффициент теплоотдачи …   Энциклопедический словарь по металлургии

• over all heat transfer coefficient — šilumos perdavimo koeficientas statusas T sritis Energetika apibrėžtis Dydis, apibūdinantis šilumos mainų pro paviršių intensyvumą ir parodantis, koks šilumos kiekis perduodamas nuo vieno šilumnešio kitam per paviršiaus ploto vienetą per laiko… …   Aiškinamasis šiluminės ir branduolinės technikos terminų žodynas

• Heat transfer — is a discipline of thermal engineering that concerns the exchange of thermal energy from one physical system to another. Heat transfer is classified into various mechanisms, such as heat conduction, convection, thermal radiation, and phase change …   Wikipedia

• Convective heat transfer — See also: Heat transfer and convection This figure shows a calculation for thermal convection. Colors closer to red are hot areas and colors closer to blue are cold areas. In this figure, a hot, less dense lower boundary layer sends plumes… …   Wikipedia

• surface coefficient of heat transfer — paviršiaus šilumos perdavos koeficientas statusas T sritis Standartizacija ir metrologija apibrėžtis Apibrėžtį žr. priede. priedas( ai) Grafinis formatas atitikmenys: angl. surface coefficient of heat transfer rus. коэффициент поверхностной… …   Penkiakalbis aiškinamasis metrologijos terminų žodynas

• surface coefficient of heat transfer — paviršiaus šilumos perdavos koeficientas statusas T sritis fizika atitikmenys: angl. surface coefficient of heat transfer vok. Wärmeübergangskoeffizient der Oberfläche, m rus. коэффициент поверхностной теплопередачи, m pranc. coefficient de… …   Fizikos terminų žodynas