1998 Esso Longford gas explosion
The 1998 Esso Longford gas explosion was a catastrophic industrial accident which occurred at the
Essonatural gas plant at Longford in the Australian state of Victoria's Gippslandregion. On 25 September 1998, an explosion took place at the plant, killing two workers and injuring eight. Gas supplies to the state of Victoria were severely affected for two weeks.
In 1998, the Longford gas plant was owned by a joint partnership between Esso and BHP. Esso was responsible for the operation of the plant. Esso was a wholly owned subsidiary of US based company Exxon, which has since merged with Mobil, becoming
ExxonMobil. BHP has since merged with UK based Billiton becoming BHP Billiton.
Built in 1969, the plant at Longford is the onshore receiving point for oil and natural gas output from production platforms in
Bass Strait. The Longford Gas Plant Complex consists of three gas processing plants and one crude oil stabilisation plant. It was the primary provider of natural gas to Victoria, and provided some supply to New South Wales.
Normal processing procedure
The feed from the Bass Strait platforms consists of liquid and gaseous
hydrocarbons, water(H2O) and hydrogen sulfide(H2S). The water and H2S are removed before reaching the plant, leaving a hydrocarbon stream to be the feed to Gas Plant 1. This stream contained both gaseous and liquid components. The liquid component was known as "condensate". The LPG is further extracted by means of a shell and tube heat exchanger, in which heated "lean oil" and cold "rich oil" (oil which has absorbed LPG) are pumped into the exchanger, cooling the lean oil and heating the rich oil.
Explosion at Longford
During the morning of Friday 25 September 1998, a pump supplying heated lean oil to heat exchanger GP905 in Gas Plant No. 1 went offline for four hours, due to an increase in flow from the Marlin Gas Field which caused an overflow of condensate in the absorber.
A heat exchanger is a vessel that allows the transfer of heat from a hot stream to a cold stream, and so does not operate at a single temperature, but experiences a range of temperatures throughout the vessel. Temperatures throughout GP905 normally ranged from 60 °C to 230 °C (140 °F to 446 °F). Investigators estimated that, due to the failure of the lean oil pump, parts of GP905 experienced temperatures as low as convert|-48|°C|°F|0. Ice had formed on the unit, and it was decided to resume pumping heated lean oil in to thaw it. When the lean oil pump resumed operation, it pumped oil into the heat exchanger at convert|230|°C|°F|0 - the temperature differential caused a brittle fracture in the exchanger (GP905) at 12.26pm.
About 10 metric tonnes of hydrocarbon vapour were immediately vented from the rupture. A vapour cloud formed and drifted downwind. When it reached a set of heaters 170 metres away, it ignited. This caused a
deflagration(a burning vapour cloud). The flame front burnt its way through the vapour cloud, without causing an explosion. When the flamefront reached the rupture in the heat exchanger, a fierce jet fire developed that lasted for two days.
The rupture of GP905 led to other releases and minor fires. The main fire was an intense jet fire emanating from GP905. There was no blast wave - the nearby control room was undamaged. Damage was localised to the immediate area around and above the GP905 exchanger.
Peter Wilson and John Lowery were killed in the accident and eight others were injured.
The fire at the plant was not extinguished until two days later. The Longford plant was shut down immediately, and the state of Victoria was left without its primary gas supplier. Within days, the
Victorian Energy Network Corporationshut down the state's entire gas supply. The sudden crisis was devastating to Victoria's economy, crippling industry and the commercial sector (in particular, the hospitality industry which relied on natural gas for cooking). Loss to industry during the crisis was estimated at around AUD$1.3 billion.
Natural gas is also widely used residentially in Victoria for hot water and gas heating, and Victorians endured 20 days of cold showers and chilly nights.
Gas supplies to Victoria were resumed on
14 October. Many Victorians were outraged and upset to discover only minor compensation on their next gas bill, with the average compensation figure being only around $10.
Royal Commissionwas called into the explosion at Longford, headed by former High Court judge Daryl Dawson. The Commission sat for 53 days, commencing with a preliminary hearing on 12 November 1998and concluding with a closing address by Counsel Assisting the Royal Commission on 15 April 1999.
Esso initially blamed the accident on worker negligence, in particular Jim Ward, one of the panel workers on duty on the day of the explosion. The findings of the Royal Commission, however, cleared Ward of any negligence or wrong-doing. Instead, the Commission found Esso fully responsible for the accident:
:"The causes of the accident on 25 September 1998 amounted to a failure to provide and maintain so far as practicable a working environment that was safe and without risks to health. This constituted a breach or breaches of Section 21 of the
Occupational Health and Safety Act 1985."
Other findings of the Royal Commission included:
*the Longford plant was poorly designed, and made isolation of dangerous vapours and materials very difficult;
*inadequate training of personnel in normal operating procedures of a hazardous process;
*excessive alarm and warning systems had caused workers to become desensitised to possible hazardous occurrences;
*the relocation of plant engineers to
Melbournehad reduced the quality of supervision at the plant;
*poor communication between shifts meant that the pump shutdown was not communicated to the following shift.
Certain managerial shortcomings were also identified:
*the company had neglected to commission a HAZOP (HAZard and OPerability) analysis of the heat exchange system, which would almost certainly have highlighted the risk of tank rupture caused by sudden temperature change;
*Esso's two-tiered reporting system (from operators to supervisors to management) meant that certain warning signs such as a previous similar incident (on 28 August) were not reported to the appropriate parties;
*the company's "safety culture" was more oriented towards preventing lost time due to accidents or injuries, rather than protection of workers and their health.
Esso was taken to the
Supreme Court of Victoriaby the Victorian WorkCover Authority. The jury found the company guilty of eleven breaches of the Occupational Health and Safety Act 1985, and Justice Philip Cummins imposed a record fine of $2 million in July 2001.
In addition, a class action was taken on behalf of businesses, industries and domestic users who were financially affected by the gas crisis. The class action went to trial in the Supreme Court on
4 September 2002, and was eventually settled in December 2004 when Esso was ordered to pay $32.5million to businesses which suffered property damage as a result of the incident.
Following the Longford accident, Victoria introduced the Major Hazard Facilities Regulations to regulate safety at plants that contain major chemical hazards. These regulations impose a so-called "non-prescriptive" regime on facility operators, requiring them to "demonstrate" control of major chemical hazards via the use of a Safety Management System and a Safety Case.
Other states have also implemented similar regulatory regimes.
*Hopkins, Andrew. "Lessons From Longford: The Esso Gas Plant Explosion", CCH Australia Limited, 2000. ISBN 1-86468-422-4
* [http://web.archive.org/web/20070622023036/http://www.coronerscourt.vic.gov.au/CA256902000FE154/Lookup/Coronial_Findings_of_Importance/$file/LONGFORD.pdf Victorian Coroner's Report into the Longford Gas Explosion] (from
* [http://www.netbay.com.au/~jpom/Learnings%20from%20accidents/general%20articles/esso_longford_verdicts.doc Implications of the Esso Longford verdicts on the engineering profession]
* [http://www1.worksafe.vic.gov.au/vwa/vwa044-021.nsf/docsbyUNID/BF69A0ECBC397EFACA2572E6000222E4/$file/VWA_Major+Hazard+Guide_P5.pdf Major Hazard Facilities] - Worksafe
Wikimedia Foundation. 2010.
Look at other dictionaries:
Longford (disambiguation) — Longford may refer to:Places;Ireland *County Longford, a small county in Ireland *Longford, County Longford s county town *Longford (constituency), constituencies in the UK parliament and the Dáil Éireann;Australia *Longford, Victoria, a town in… … Wikipedia
1998 in Australia — Infobox Australian year monarch =Elizabeth II governor general = William Deane pm =John Howard population = 18,711,271 australian = elections =Federal, ACT, QLD, NSW See also: 1997 in Australia, other events of 1998, 1999 in Australia See also: * … Wikipedia
Longford, Victoria — Infobox Australian Place | type = town name = Longford state = vic caption = lga = Shire of Wellington postcode = 3851 est = pop = 929 elevation= maxtemp = mintemp = rainfall = stategov = Gippsland South fedgov = Gippsland dist1 = 216 dir1 = E… … Wikipedia
Royal Commission — The term Royal Commission may also be used in the United Kingdom to describe the group of Lords Commissioners who may act in the stead of the Sovereign to grant Royal Assent to legislation passed by Parliament. In Commonwealth realms and other… … Wikipedia
Brian Walters — SC is a prominent Melbourne barrister, Senior Counsel, and civil liberties advocate.EducationBrian Walters was born on 17 June 1954, the third of four sons born to Neville Walters and Jean Walters. He was educated at Blackburn State School, Carey … Wikipedia
List of power outages — This is a list of notable wide scale power outages.1965* The Northeast Blackout of 1965 in the USA on November 9, 1965.1974* A freak early season blizzard on October 13, 1974 caused a major power outage that affected more than a million customers … Wikipedia
Sale, Victoria — Infobox Australian Place | type = city name = Sale state = vic caption = pop = 13,350 (2006)Census 2006 AUS | id = SSC26569 | name = Sale (Urban Centre/Locality) | accessdate = 2007 10 25 | quick = on] poprank = density = est = 1851 propval =… … Wikipedia
Julian Burnside — Julian William Kennedy Burnside QC (born June 9, 1949) is an Australian barrister, human rights and refugee advocate, and author. He is known for his staunch opposition to the mandatory detention of asylum seekers, and has provided legal counsel… … Wikipedia