Fire sprinkler system
A fire sprinkler system is an
active fire protectionmeasure, consisting of a water supply, providing adequate pressure and flowrate to a water distribution piping system, onto which fire sprinklers are connected. Although historically only used in factories and large buildings, home and small building systems are now available at a relatively cost-effective price.
The world’s first sprinkler system was installed in the
Theatre Royal, Drury Lanein the United Kingdom in 1812. The systems consisted of a cylindrical airtight reservoir of 400 hogsheads(~95,000 litres) fed by a 10in (250mm) water main which branched to all parts of the theatre. A series of smaller pipes feed from the distribution pipe were pierced with a series of 1/2" (15mm) holes which pour water in the event of a fireFact|date=May 2008.
From 1852 to 1885, perforated pipe systems were used in textile mills throughout New England as a means of fire protection. However, they were not automatic systems; they did not turn on by themselves. Inventors first began experimenting with automatic sprinklers around 1860. The first automatic sprinkler system was patented by Philip W. Pratt of Abington, MA, in 1872. [ [http://www.meritsprinkler.com/history.htm SPRINKLER HISTORY] Merit Sprinkler Company ]
Henry S. Parmalee of New Haven, Connecticut is considered the inventor of the first automatic sprinkler head. Parmalee improved upon the Pratt patent and created a better sprinkler system. In 1874, he installed his fire sprinkler system into the piano factory that he owned.
Frederick Grinnellimproved Parmalee's design and in 1881 patented the automatic sprinkler that bears his name. He continued to improve the device and in 1890 invented the glass disc sprinkler, essentially the same as that in use today. [ Casey Cavanaugh Grant, PE [http://www.nfpa.org/itemDetail.asp?categoryID=500&itemID=18020&URL=About%20Us/History&cookie%5Ftest=1 The Birth of NFPA] NFPA1996 ]
Until the 1940s, sprinklers were installed almost exclusively for the protection of commercial buildings, whose owners were generally able to recoup their expenses with savings in insurance costs. Over the years, fire sprinklers have become mandatory safety equipment North America,in certain occupancies, including, but not limited to newly constructed hospitals, schools, hotels and other public buildings, subject to the local building codes and enforcement. However, outside of the US and Canada, sprinklers are rarely mandated by building codes for normal hazard occupancies which do not have large numbers of occupants (e.g. factories, process lines, retail outlets, petrol stations etc)
Sprinklers have been in use in the
United Statessince 1874, and were used in factory applications where fires at the turn of the century were often catastrophic in terms of both human and property losses. In the US, sprinklers are today required in all new high rise and underground buildings generally 75 feet (23 m) above or below fire department access, where the ability of firefighters to provide adequate hose streams to fires is limited.Fact|date=October 2007
Sprinklers may be required to be installed by
building codes, or may be recommended by insurance companies to reduce potential property losses or business interruption. Building codes in the United States for places of assembly, generally over 100 persons, and places with overnight sleeping accommodation such as hotels, nursing homes, dormitories, and hospitals usually require sprinklersFact|date=May 2008.
If building codes do not explicitly mandate the use of fire sprinklers, the code often makes it highly advantageous to install them as an optional system. Most standard US building codes (UBC and IBC included) allow for less expensive construction materials, larger floor area limitations, longer egress paths, and fewer requirements for fire rated construction in structures protected by fire sprinklers. Consequently, the total building cost it is often less by installing a sprinkler system and savings money in the other aspects of the project, as compared to building a non-sprinklered structure.
Each closed-head sprinkler is held closed by either a heat-sensitive glass bulb (see below) or a two-part metal link held together with
fusible alloy. The glass bulb or link applies pressure to a pip cap which acts as a plug which prevents water from flowing until the ambient temperature around the sprinkler reaches the design activation temperature of the individual sprinkler head. Because each sprinkler activates independently when the predetermined heat level is reached, the number of sprinklers that operate is limited to only those near the fire, thereby maximizing the available water pressure over the point of fire origin.
A sprinkler activation will do less damage than a fire department hose stream, which provide approximately 900 liters/min (250 US gallons/min). A typical sprinkler used for industrial manufacturing occupancies discharge about 75-150 litres/min (20-40 US gallons/min). However, a typical Early Suppression Fast Response (ESFR) sprinkler at a pressure of 50 psi (345 kPa) will discharge approximately 100 US gallons per minute, (380 litres per minute). In addition, a sprinkler will usually activate between one and four minutes, whereas the fire department typically takes at least five minutes to arrive at the fire site after receiving an alarm, and an additional ten minutes to set up equipment and apply hose streams to the fire. This additional time can result in a much larger fire, requiring much more water to achieve extinguishment.
Sprinkler systems are intended to either "control" the fire or to "suppress" the fire. "Control mode" sprinklers are intended to control the
heat release rateof the fire to prevent building structure collapse, and pre-wet the surrounding combustibles to prevent fire spread. The fire is not extinguished until the burning combustibles are exhausted or manual extinguishment is effected by firefighters. "Suppression mode" sprinklers (formerly known as "Early Suppression Fast Response" ( ESFR) sprinklers) are intended to result in a severe sudden reduction of the heat release rate of the fire, followed quickly by complete extinguishment, prior to manual intervention.
Wet pipe systems
By a wide margin, wet pipe sprinkler systems are installed more often than all other types of fire sprinkler systems. They also are the most reliable, because they are simple, with the only operating components being the automatic sprinklers and (commonly, but not always) the automatic alarm check valve. An automatic water supply provides water under pressure to the system piping. All of the piping is filled with water. Until sufficient heat is applied, causing one or more sprinklers to fuse (open), the automatic sprinklers prevent the water from being discharged.
Operation - When an automatic sprinkler is exposed to sufficient heat, the heat sensitive element (glass bulb or fusible link) releases, allowing water to flow from that sprinkler. Sprinklers are manufactured to react to a specific range of temperatures. Only sprinklers subjected to a temperature at or above their specific temperature rating will operate.s
Dry pipe systems
IN US building codes Dry pipe systems can only be used (by regulation [NFPA 13 2007 ed. Sections 7-2 and A7-2] ) in spaces in which the ambient temperature may be cold enough to freeze the water in a wet pipe system, rendering the system inoperable. Dry pipe systems are most often used in unheated buildings, in outside canopies attached to heated buildings (in which a wet pipe system would be provided), or in refrigerated coolers. Dry pipe systems are the second most common sprinkler system type.
Water is not present in the piping until the system operates. The piping is pressurized with air, at a "maintenance" pressure which is relatively low compared with the water supply pressure. To prevent the larger water supply pressure from forcing water into the piping, the design of the dry pipe valve (a specialized type of
check valve) intentionally includes a larger valve clapper area exposed to the maintenance air pressure, as compared to the water pressure.
Operation - When one or more of the automatic sprinklers is exposed to sufficient heat, it opens, allowing the maintenance air to vent from that sprinkler. Each sprinkler operates individually. As the air pressure in the piping drops, the
pressure differentialacross the dry pipe valve changes, allowing water to enter the piping system. Water flow from sprinklers needed to control the fire is delayed until the air is vented from the sprinklers. For this reason, dry pipe systems are usually not as effective as wet pipe systems in fire control during the initial stages of the fire.
Some view dry pipe sprinklers as advantageous for protection of collections and other water sensitive areas. This perceived benefit is due to a fear that a physically damaged wet pipe system will leak, while dry pipe systems will not. However, dry pipe systems will only provide a slight delay prior to water discharge while the air in the piping is released prior to the water filling the pipe.
Disadvantages of using dry pipe fire sprinkler systems include:
* Increased complexity - Dry pipe systems require additional control equipment and air pressure supply components which increases system complexity. This puts a premium on proper maintenance, as this increase in system complexity results in an inherently less reliable overall system (i.e., more
single failure points) as compared to a wet pipe system.
* Higher installation and maintenance costs - The added complexity impacts the overall dry-pipe installation cost, and increases maintenance expenditure primarily due to added service labor costs.
* Lower design flexibility - Regulatory requirements limit the maximum permitted size (i.e., 750 gallons) of individual dry-pipe systems, unless additional components and design efforts are provided to limit the time from sprinkler activation to water discharge to under one minute. These limitations may increase the number of individual sprinkler systems (i.e., served from a single riser) that must be provided in the building, and impact the ability of an owner to make system additions.
* Increased fire response time - A maximum of 60 seconds is allowed by regulatory requirements from the time a sprinkler opens until water is discharged onto the fire. This delay in
fire suppressionresults in a larger fire prior to control, producing increased content damage.
corrosionpotential - Following operation or testing, dry-pipe sprinkler system piping is drained, but residual water collects in piping low spots, and moisture is also retained in the atmosphere within the piping. This moisture, coupled with the oxygen available in the compressed air in the piping, increases pipe internal wall corrosion rates, possibly eventually leading to leaks. The internal pipe wall corrosion rate in wet pipe systems (in which the piping is constantly full of water) is much lower, reducing the amount of oxygen available for the corrosion process.
"Deluge" systems are systems that have open sprinklers, i.e. the heat sensing operating element is removed during installation, so that all sprinklers connected to the water piping system are open. These systems are used for special hazards where rapid fire spread is a concern, as they provide a simultaneous application of water over the entire hazard. They are commonly seen as preventative measures to prevent egress of fire from an external source (eg hi-rise windows, warehouse bay entries, over openings in a fire-rated wall)
Water is not present in the piping until the system operates. Because the sprinkler orifices are open, the piping is at atmospheric pressure. To prevent the water supply pressure from forcing water into the piping, a "deluge valve" is used in the water supply connection, which is a mechanically latched valve. It is a non-resetting valve, and stays open once tripped.
Because the heat sensing elements present in the automatic sprinklers have been removed (resulting in open sprinklers), the deluge valve must be opened as signaled by a specialized fire alarm system. The type of fire alarm initiating device is selected mainly based on the hazard (e.g.,
smoke detectors, heat detectors, or optical flame detectors). The initiation device signals the fire alarm panel, which in turn signals the deluge valve to open. Activation can also be manual, depending on the system goals. Manual activation is usually via an electric or pneumatic fire alarm pull station, which signals the fire alarm panel, which in turn signals the deluge valve to open.
Operation - Activation of a fire alarm initiating device, or a manual pull station, signals the fire alarm panel, which in turn signals the deluge valve to open, allowing water to enter the piping system. Water flows from all sprinklers simultaneously.
Pre-action sprinkler systems are specialized for use in locations where accidental activation is undesired, such as in
museums with rare art works, manuscripts, or books; and Data Centers, for protection of computer equipment from accidental water discharge.
Pre-action systems are hybrids of wet, dry, and deluge systems, depending on the exact system goal. There are two main sub-types of pre-action systems: single interlock, and double interlock. The operation of single interlock systems are similar to dry systems except that these systems require that a “preceding” and supervised event (typically the activation of a heat or smoke detector) takes place prior to the “action” of water introduction into the system’s piping due to opening of the pre-action valve (which is a mechanically latched valve). Once the fire is detected by the fire alarm system, the system is essentially converted from a dry system into a wet system. Or, if an automatic sprinkler operated prior to the fire being detected by the fire alarm system, water will be allowed into the piping, and will discharge water from the sprinkler.
The operation of double interlock systems are similar to deluge systems except that automatic sprinklers are used. These systems require that
botha “preceding” and supervised event (typically the activation of a heat or smoke detector), and an automatic sprinkler activation take place prior to the “action” of water introduction into the system’s piping. There is also a little used variation known as Non-Interlock.
Foam water sprinkler systems
A foam water fire sprinkler system is a special application system, discharging a mixture of water and low expansion
foamconcentrate, resulting in a foam spray from the sprinkler. These systems are usually used with special hazards occupancies associated with high challenge fires, such as flammable liquids, and airport hangars. Operation is as described above, depending on the system type into which the foam is injected.
"Water spray" systems are operationally identical to a deluge system, but the piping and discharge nozzle spray patterns are designed to protect a uniquely configured hazard, usually being three dimensional components or equipment (i.e., as opposed to a deluge system, which is designed to cover the horizontal floor area of a room). The nozzles used may not be listed fire sprinklers, and are usually selected for a specific spray pattern to conform to the three dimensional nature of the hazard (e.g., typical spray patterns being oval, fan, full circle, narrow jet). Examples of hazards protected by water spray systems are electrical transformers containing a flammable liquid as a cooling oil, or tanks containing a flammable gas such as hydrogen.
DesignThis chart from the
indicates the colour
of the bulb and the
Most sprinkler systems installed today are designed using an area and density approach. First the building use and building contents are analyzed to determine the level of fire hazard. Usually buildings are classified as light hazard, ordinary hazard group 1, ordinary hazard group 2, extra hazard group 1, or extra hazard group 2. After determining the hazard classification, a design area and density can be determined by referencing tables in the
National Fire Protection Association(NFPA) standards. The design area is a theoretical area of the building representing the worst case area where a fire could burn. The design density is a measurement of how much water per square foot of floor area should be applied to the design area. For example, in an office building classified as light hazard, a typical design area would be 1500 square feet and the design density would be 0.1 gallons per minute per square foot or a minimum of 150 gallons per minute applied over the 1500 square foot design area. Another example would be a manufacturing facility classified as ordinary hazard group 2 where a typical design area would be 1500 square feet and the design density would be 0.2 gallons per minute per square foot or a minimum of 300 gallons per minute applied over the 1500 square foot design area.
After the design area and density have been determined, calculations are performed to prove that the system can deliver the required amount of water over the required design area. These calculations account for all of the pressure that is lost or gained between the water supply source and the sprinklers that would operate in the design area. This includes pressure losses due to friction inside the piping and losses or gains due to elevational differences between the source and the discharging sprinklers. Sometimes momentum pressure from water velocity inside the piping is also calculated. Typically these calculations are performed using computer software but before the advent of computer systems these sometimes complicated calculations were performed by hand. This skill of calculating sprinkler systems by hand is still required training for a sprinkler system design
Technologistwho seeks senior level certification from engineering certification organizations such as the National Institute for Certification in Engineering Technologies(NICET).
Sprinkler systems in residential structures are becoming more common as the cost of such systems becomes more practical and the benefits become more obvious. Residential sprinkler systems usually fall under a residential classification separate from the commercial classifications mentioned above. A commercial sprinkler system is designed to protect the structure and the occupants from a fire. Most residential sprinkler systems are primarily designed to suppress a fire in such a way to allow for the safe escape of the building occupants. While these systems will often also protect the structure from major fire damage, this is a secondary consideration. In residential structures sprinklers are often omitted from closets, bathrooms, balconies, garages and attics because a fire in these areas would not usually impact the occupant's escape route.
If water damage or water volume is of particular concern, a technique called "Water Mist Fire Suppression" may be an alternative. This technology has been under development for over 50 years. It hasn't entered general use, but is gaining some acceptance on ships and in a few residential applications. Mist suppression systems work by lowering the temperature of a burning area through evaporation rather than "soaking". As such, they may be designed to only slow the spread of a fire and not extinguish it. Some tests, that may or may not be biased, showed the cost of resulting fire and water damage with such a system installed to be dramatically less than conventional sprinkler systems. [http://darwin.nap.edu/books/0309057825/html/85.html]
In 2006, the hardware costs of sprinkler systems run from US$2 - $5 per square foot ($50/m²), depending on type and location. However, specialty systems may cost as much as $10/square foot ($100/m²).Fact|date=December 2007 Systems can be installed during construction or retrofitted. Some communities have laws requiring residential sprinkler systems, where large municipal
hydrantwater supplies ("fire flows") are not available. Nationwide in the United States, one and two-family homes generally do not require fire sprinkler systems, although the overwhelming loss of life due to fires occurs in these spaces. Residential sprinkler systems are relatively inexpensive (about the same per square foot as carpeting or floor tiling), but require larger water supply piping than is not normally installed in homes, so retrofitting is usually cost prohibitive.
According to the National Fire Protection Association (NFPA), fires in hotels with sprinklers averaged 78% less damage than fires in hotels without them (
1983- 1987). The NFPA says the average loss per fire in buildings with sprinklers was $2,300, compared to an average loss of $10,300 in unsprinklered buildings. The NFPA adds that there is no record of a fatality in a fully sprinklered building outside the point of fire origin. However, in a purely economic comparison, this is not a complete picture; the total costs of fitting, and the costs arising from non-fire triggered release must be factored.
The NFPA states that it "has no record of a fire killing more than two people in a completely sprinklered building where a sprinkler system was properly operating, except in an
explosionor flash fireor where industrial fire brigade members or employees were killed during fire suppression operations."
The world's largest fire sprinkler manufacturer is the SimplexGrinnell division of
Tyco International, other manufacturers / suppliers include [http://www.vikinggroupinc.com The Viking Corporation] , [http://www.victaulic.com/content/ Victaulic] , [http://nni.8m.com NNI Inc] , [http://www.pup-sprinkleranlagen.de P.u.P. Feuerschutz und Anlagenbau GmbH] and [http://www.reliablesprinkler.com Reliable Sprinkler Company] .
Active fire protection
Passive fire protection
Listing and approval use and compliance
Fire protection engineering
* [http://www.olyfire.com/history.html Fire Sprinkler history]
* [http://www.ua.org/ The United Association of Journeymen and Apprentices of the Plumbing and Pipe Fitting Industry of the United States and Canada]
* [http://www.sprinklernet.org American Fire Sprinkler Association]
* [http://www.nfsa.org National Fire Sprinkler Association]
* [http://www.nfpa.org National Fire Protection Association]
* [http://www.bafsa.org.uk British Automatic Fire Sprinkler Association]
* [http://www.bvfa.de/frameset.asp Bundesverband Technischer Brandschutz e.V.]
Wikimedia Foundation. 2010.
Look at other dictionaries:
Fire suppression system — Fire suppression systems are used in conjunction with smoke detectors and fire alarm systems to improve and increase public safetyTypes* Fire sprinkler systems (wet, dry, pre action, and deluge) * Gaseous agents * Wet and dry chemical… … Wikipedia
Fire-control system — Note: the term fire control may also refer to means of stopping a fire, such as sprinkler systems. A fire control system is a computer, often mechanical, which is designed to assist a weapon system in hitting its target. It performs the same task … Wikipedia
Fire sprinkler — A fire sprinkler is the part of a fire sprinkler system that discharges water when the effects of a fire have been detected, such as when a predetermined temperature has been reached. History Henry S. Parmelee of New Haven, CT created and… … Wikipedia
Fire sprinkler (disambiguation) — A Fire sprinkler can refer to * The actual device that dischanges water, also known as a sprinkler head or fire sprinkler head; * The complete Fire sprinkler system … Wikipedia
sprinkler system — n. 1. a system of pipes and attached nozzles carrying water or other extinguishing fluid throughout a building for protection against fire: it usually operates automatically when exposed to abnormal heat 2. a system of pipes and nozzles, often… … English World dictionary
sprinkler system — noun a system for extinguishing fires; water from a network of overhead pipes is released through nozzles that open automatically with the rise in temperature • Hypernyms: ↑system • Part Meronyms: ↑nozzle, ↑nose, ↑siamese, ↑siamese connection * * … Useful english dictionary
sprinkler system — apparatus for automatically extinguishing fires in a building, consisting of a system of water pipes in or below the ceilings, with valves or sprinklers usually made to open automatically at a certain temperature. [1880 85] * * * ▪ fire control… … Universalium
sprinkler system — An overhead arrangement of water pipes and sprinklers, constructed and maintained in a building as a protection against fire, water being turned on automatically upon a rise in temperature consequent to the starting of a fire … Ballentine's law dictionary
sprinkler system — noun Date: circa 1909 a system for protecting a building against fire by means of overhead pipes which convey an extinguishing fluid (as water) to heat activated outlets … New Collegiate Dictionary
Fire protection — is the study and practice of mitigating the unwanted effects of fires [NFPA Fire Protection Handbook, pg. 2 19] . It involves the study of the behaviour, compartmentalisation, suppression and investigation of fire and its related emergencies, as… … Wikipedia