Micro hydro is a term used for hydroelectric power installations that typically produce up to 100 kW of electricity. These installations can provide power to an isolated home or small community, or are sometimes connected to electric power networks. There are many of these installations around the world, particularly in developing nations as they can provide an economical source of energy without the purchase of fuel. Micro hydro systems complement photovoltaic solar energy systems because in many areas, water flow, and thus available hydro power, is highest in the winter when solar energy is at a minimum. Micro hydro is frequently accomplished with a pelton wheel for high head, low flow water supply. The installation is often just a small dammed pool, at the top of a waterfall, with several hundred feet of pipe leading to a small generator housing.
Construction and characteristics
Construction details of a microhydro plant are site-specific, but the common elements of all hydroelectric plants are present. A supply of water is needed — this can be a mountain stream, or a river. Usually microhydro installations do not have a dam and reservoir, relying on a minimal flow of water to be available year-round. Sometimes an existing mill-pond or other artificial reservoir is available and can be adapted for power production. An intake structure is required to screen out floating debris and fish, using a screen or array of bars to keep out large objects. In temperate climates this structure must resist ice as well. The intake may have a gate to allow the system to be dewatered for inspection and maintenance.
Water withdrawn from the source must move along a power canal or a pipe (penstock) to the turbine. If the water source and turbine are far apart, the construction of the penstock may be the largest part of the costs of construction. In mountainous areas, access to the route of the penstock may provide considerable challenges.
At the turbine, a controlling valve is installed to regulate the flow and the speed of the turbine. The turbine converts the flow and pressure of the water to mechanical energy; the water emerging from the turbine returns to the natural watercourse along a tailrace channel.
The turbine turns a generator, which is then connected to electrical loads; this might be directly connected to the power system of a single building in very small installations, or may be connected to a community distribution system for several homes or buildings.
Regulation and operation
Typically, an automatic controller operates the turbine inlet valve to maintain constant speed (and frequency) when the load changes on the generator. In a system connected to a grid with multiple sources, the turbine control ensures that power always flows out from the generator to the system. The frequency of the alternating current generated needs to match the local standard utility frequency. In some systems, if the useful load on the generator is not high enough, a load bank may be automatically connected to the generator to dissipate energy not required by the load; while this wastes energy, it may be required if its not possible to stop the water flow through the turbine.
An induction generator always operates at the grid frequency irrespective of its rotation speed; all that is necessary is to ensure that it is driven by the turbine faster than the synchronous speed so that it generates power rather than consuming it. Other types of generator require a speed control systems for frequency matching.
With the availability of modern power electronics it is often easier to operate the generator at an arbitrary frequency and feed its output through an inverter which produces output at grid frequency. Power electronics now allow the use of permanent magnet alternators that produce wild AC to be stabilised. This approach allows low speed / low head water turbines to be competitive; they can run at the best speed for extraction of energy, and the power frequency is controlled by the electronics instead of the generator.
Very small installations, a few kilowatts or smaller, may generate direct current and charge batteries for peak use times.
Several different types of water turbines can be used in micro hydro installations, selection depending on the head of water, the volume of flow, and such factors as availability of local maintenance and transport of equipment to the site. For mountainous regions where a waterfall of 50 meters or more may be available, a Pelton wheel can be used. For low head installations, Francis or propeller-type turbines are used. Very low head installations of only a few meters may use propeller-type turbines in a pit. The very smallest micro hydro installations may successfully use industrial centrifugal pumps, run in reverse as prime movers; while the efficiency may not be as high as a purpose-built runner, the relatively low cost makes the projects economically feasible.
In low-head installations, maintenance and mechanism costs often become important. A low-head system moves larger amounts of water, and is more likely to encounter surface debris. For this reason a Banki turbine also called Ossberger turbine , a pressurized self-cleaning crossflow waterwheel, is often preferred for low-head microhydropower systems. Though less efficient, its simpler structure is less expensive than other low-head turbines of the same capacity. Since the water flows in, then out of it, it cleans itself and is less prone to jam with debris.
Reverse Archimedes' screw : two low-head schemes in England, Settle Hydro and Torrs Hydro use a Archimedes' screw which is another debris-tolerant design. Efficiency 85%.
Francis and propeller turbines.
Water wheel : advanced hydraulic water wheels and hydraulic wheel-part reaction turbine can have hydraulic efficiencies of 67% and 85% respectively.
Gravitation water vortex power plant : part of the river flow at a weir or natural water fall is diverted into a round basin with a central bottom exit that creates a vortex. A simple rotor (and connected generator) is moved by the kinetic energy. Efficiencies of 83% down to 64% at 1/3 part flow.
- ^ Micro Hydro in the fight against poverty
- ^ Gorlov A.M., Development of the helical reaction hydraulic turbine. Final Technical Report, The US Department of Energy, August 1998, The Department of Energy's (DOE) Information Bridge: DOE Scientific and Technical Information.
- ^ Ashden Awards. "Micro-hydro". http://www.ashdenawards.org/micro-hydro. Retrieved 2009-06-29.
- ^ http://www.vlh-turbine.com/EN/html/History.htm
- Portal on microhydro power
- SMART - Strategies to proMote small scAle hydro electRicity producTion in Europe (project financed by the European Commission, involves Italy, Croatia, Norway, Greece and Austria)
- Micro Hydro information, Dorado Vista ranch application
- European Small Hydropower Association
- Hydropower Prospector, Idaho National Engineering Laboratory
- Checklist on Small Hydropower, Mini Hydraulics Laboratory (Switzerland), European Small Hydropower Association
- Ashden Awards hydro power winners
- Example of a new Scottish Highland micro hydro system
- Home built micro hydro project
Wikimedia Foundation. 2010.
Look at other dictionaries:
Micro combined heat and power — or micro CHP is an extension of the now well established idea of cogeneration to the single/multi family home or small office building. Contents 1 Overview 2 Micro CHP systems 3 Engine types and technologies … Wikipedia
Micro-centrale — Petite centrale hydroélectrique Turbine de type Francis avec sa génératrice Une petite centrale hydroélectrique est une centrale électrique utilisant l énergie hydraulique pour produire de l électricité à petite échelle. Cette électricité peut… … Wikipédia en Français
Hydro-allergie — Hydroallergie Il s agit d une allergie à l eau chaude, froide, douce, salée, aux micro organismes présents dans l eau (algues, coraux, plancton, poissons...) et à la suite d une immersion complète ou partielle du corps. Elle se traduit par des… … Wikipédia en Français
Small hydro — is the development of hydroelectric power on a scale serving a small community or industrial plant. The definition of a small hydro project varies but a generating capacity of up to 10 megawatts (MW) is generally accepted as the upper limit of… … Wikipedia
Pico hydro — is a term used for hydroelectric power generation of under 5kW. It is useful in small, remote communities that require only a small amount of electricity for example, to power one or two lightbulbs in a house, or a radio, for part of the day.… … Wikipedia
Damless hydro — or Damless hydro electric is a renewable technology based on capturing the kinetic energy of rivers, channels of chutes, spillways, irrigation systems, tides and oceans without the use of dams [cite web… … Wikipedia
BC Hydro — Infobox Company company name = BC Hydro company company type = Crown Corporation company slogan = For Generations foundation = 1961 location = British Columbia, Canada key people = Bob Elton, President CEO [ [http://bchydro.com/info/board… … Wikipedia
Solution hydro-alcoolique — Conditionnement de solution hydro alcoolique en gel Les solutions hydro alcooliques (encore nommées par acronymie SHA ou SHAL) sont des solutions antiseptiques cutanées. Elles sont employées afin d assurer l hygiène des mains, notamment lors des… … Wikipédia en Français
Pumped-storage hydroelectricity — Hydro storage redirects here. For storage of water for other purposes, see Reservoir. Diagram of the TVA pumped storage facility at Raccoon Mountain Pumped Storage Plant … Wikipedia
Hydroelectricity — The Gordon Dam in Tasmania is a large hydro facility, with an installed capacity of 430 MW … Wikipedia