A lightning rod (USA) or lightning conductor (UK) is a single component in a
lightning protection system. In addition to rods placed at regular intervals on the highest portions of a structure, a lightningprotection system typically includes a rooftop network of conductors, multiple conductive paths from the roof to the ground, bonding connections to metallic objects within the structure and a grounding network. The actual rooftop lightning rod is a metal strip or rod, usually of copper or aluminum. Lightning protection systems are installed on structures, trees, monuments, bridges and even water vessels to protect from lightning damage. Individual lightning rods are sometimes called finials, air terminals or strike termination devices. The United States Patent Officelabels "Lightning protectors" in Class 174 (Electricity: conductors and insulators), Subclass 2 (Lightning protectors) and Subclass 3 (Rods).
Lightning damage has been with humanity since people started building structures. Early structures made of wood and stone tended to be short and in valleys and as a result lightning hit rarely. As buildings became taller, lightning became a significant threat. Lightning can damage structures made of most materials (masonry, wood, concrete and even steel) as the huge currents involved can heat materials, and especially water to high temperatures causing fire, loss of strength and explosions from superheated steam and air.
The church tower of many European cities, usually the highest structure, was the building often hit by lightning. Early on, Christian churches tried to prevent the occurrence of the damaging effects of lightning by prayers. Priests prayed,: "temper the destruction of hail and cyclones and the force of tempests and lightning; check hostile thunders and great winds; and cast down the spirits of storms and the powers of the air."Peter Ahlwardts ("Reasonable and Theological Considerations about Thunder and Lightning", 1745) advised individuals seeking cover from lightning to go anywhere except in or around a church. [Seckel, Al, and John Edwards, " [http://www.evolvefish.com/freewrite/franklgt.htm Franklin's Unholy Lightning Rod] ". 1984.] In Europe, the lightning rod was invented by
Václav Prokop Divišbetween 1750- 1754.
According to some speculations, lightning conductors were used in Nevyansk tower, where the roof of the tower is crowned with a metallic rod in the shape of a
gilded spherewith spikes. If the Nevyansk Tower were built somewhere between 1725 and 1732, then the Russian craftmen created the first lightning rod some 25 years before Benjamin Franklin. Since nothing is known about the architect or origin of the building (not even the time of construction is clear), the true purpose and intent behind the metal rooftop remains unknown.
United States, the pointed lightning rod conductor, also called a "lightning attractor" or "Franklin rod," was invented by Benjamin Franklinin 1749 as part of his groundbreaking explorations of electricity. Franklin speculated that, with an ironrod sharpened to a point at the end,
:"The electrical fire would, I think, be drawn out of a cloud silently, before it could come near enough to strike [...] ."
Franklin speculated about lightning rods for several years before his reported kite experiment. This experiment, in fact, took place because he was tired of waiting for Christ Church in
Philadelphiato be completed so he could place a lightning rod on top of it. There was some resistance from churches who felt that it was defying divine will to install these rods. Franklin countered that there is no religious objection to roofs on buildings to resist precipitation, so lightning, which he proved to be simply a giant electrical spark, should be no different. As an act of philanthropy, Franklin decided against patenting the invention.
19th centurythe lightning rod became a symbol of American ingenuity and a decorative motif. Lightning rods were often embellished with ornamental glassballs [" [http://www.antiquebottles.com/lightningrod/fame.html Antique Lightning Rod Ball Hall of Fame] ". Antique Bottle Collectors Haven. (glass lightning balls collection)] (now prized by collectors). The ornamental appeal of these glass balls has also been incorporated into weather vanes.
Balls of solid glass occasionally were used in a method purported to prevent lightning strikes to ships. Although this failed to work, it is worth noting because it reveals a lot about pre-scientific thought. The basic principle was that glass objects, being non-conductors, are seldom struck by lightning. Therefore, goes the theory, there must be something about glass that repels lightning. Hence the best method for preventing a lightning strike to a wooden ship was to bury a small solid glass ball in the tip of the highest mast. The random behavior of lightning ensured that the method gained a good bit of credence even after the development of the marine lightning rod soon after Franklin's initial work.
Nikola Tesla's US patent|1,266,175 was an improvement in lightning protectors. The patent was granted due to a fault in Franklin's original theory of operation; the pointed lightning rod actually ionizes the air around itself, rendering the air conductive, which in turn raises the probability of a strike. Many years after receiving his patent, in 1919 Dr. Tesla wrote an article for The Electrical Experimenterentitled " Famous Scientific Illusions", in which he explains the logicof Franklin's pointed lightning rod and discloses his improved method and apparatus.
Some DuPont Explosives manufacturing sites, which were surrounded by pine trees, used various lightning protection devices. During the 1950s, DuPont made nitroglycerin in some buildings and moved it in 'Angel Buggies' to the packing building. Employees at those sites were very sensitive to potential lightning strikes.Fact|date=February 2007
In the 1990s, the 'lightning points' were replaced as originally constructed when the statue of Freedom atop the United States Capitol building in Washington, D.C. was restored.Fact|date=April 2007 The statue was designed with multiple devices that are tipped with platinum. The Washington Monument also was equipped with multiple lightning points, [ [http://www.tms.org/pubs/journals/JOM/9511/Binczewski-9511.html#RTFToC5 The Point of a Monument: A History of the Aluminum Cap of the Washington Monument: The Functional Purpose] ] and the rays that radiate from the crown of the Statue of Liberty in New York Harbor constitute a lightning-dissipation device. Fact|date=April 2007
Conventional lightning rods are connected via a low-resistance wire or cable to the earth or water below, where the charge may be safely dissipated. Diversion is a misnomer; modern systems intercept the charge that terminates on a structure and carry it to the ground. The diversion theory states that the lightning rod protects a structure purely because it is grounded, and thus a lightning strike that happens to attach to the protector will be diverted around the structure and "earthed" through a grounding cable or conductor. [US patent|4429341, "Lightning protection for external surface composite material of an aircraft", Charles H. King.] There is some uncertainty as to why a lightning strike might preferentially attach to a lightning protector; the leading assumption is that the air near the protector becomes ionized and thus conductive due to the intense electric field. Various manufacturers make these claims.
telegraphyand telephony, a lightning arrester [Alternatively, they are called "paratonneres" from the French terminology.] is placed where wires enter a structure, preventing damage to electronic instruments within and ensuring the safety of individuals near them. Lightning arresters, also called surge protectors, are devices that are connected between each electrical conductor in a power and communications systems and the Earth. These provide a short circuitto the ground that is interrupted by a non-conductor, over which lightning jumps. Its purpose is to limit the rise in voltage when a communications or power line is struck by lightning.
The non-conducting material may consist of a semi-conducting material such as silicon carbide or zinc oxide, or a spark gap. Primitive varieties of such spark gaps are simply open to the air, but more modern varieties are filled with dry gas and have a small amount of radioactive material to encourage the gas to ionize when the voltage across the gap reaches a specified level. Other designs of lightning arresters use a glow-discharge tube (essentially like a neon glow lamp) connected between the protected conductor and ground, or myriad voltage-activated solid-state switches called
varistors or MOVs. Lightning arresters built for substation use are impressive devices, consisting of a porcelain tube several feet long and several inches in diameter, filled with disks of zinc oxide. A safety port on the side of the device vents the occasional internal explosion without shattering the porcelain cylinder.
Electric power system lightning protection
High-tension power lines carry a lighter conductor (sometimes called a 'pilot' or 'shield') wire over the main power conductors. This conductor is grounded at various points along the link, or insulated from the tower structures by small insulators that are easily jumped by lightning voltages. The latter allows the pilot wire to be used for communications purposes, or to carry current for aircraft clearance lights. Electrical substations may have a web of grounded wires covering the whole plant.
Lightning protection of mast radiators
Mast radiators are insulated from the ground by a gap at the base. When lightning hits the mast, it jumps this gap. A small inductivity in the feed line between the mast and the tuning unit (usually one winding) limits the voltage increase, protecting the transmitter from dangerously high voltages.The transmitter must be equipped with a device to monitor the antenna's electrical properties. This is very important, as a charge could remain after a lightning strike, damaging the gap or the insulators.The monitoring device switches off the transmitter when the antenna shows incorrect behavior, e.g. as a result of undesired electrical charge. When the transmitter is switched off, these charges dissipate. The monitoring device makes several attempts to switch back on. If after several attempts the antenna continues to show improper behavior, possibly as result of structural damage, the transmitter remains switched off.
Lightning conductors and grounding precautions
Ideally, the underground part of the assembly should reside in an area of high ground conductivity. If the underground cable is able to resist
corrosionwell, it can be covered in saltto improve its electrical connection with the ground. While the electrical resistance of the lightning conductor between the air terminal and the Earth is concerning, the inductive reactance of the conductor could be more important. For this reason, the down conductor route is kept short, and any curves have a large radius. If these measures are not taken, lightning current may arc over an obstruction, resistive or reactive, that it encounters in the conductor. At the very least, the arc current will damage the lightning conductor and can easily find another conductive path, such as building wiring or plumbing, and cause fires or other disasters. Grounding systems without low resistivity to the ground can still be effective in protecting a structure from lightning damage. When ground soil has poor conductivity, is very shallow, or non-existent, a grounding system can be augmented by adding ground rods, counterpoise (ground ring) conductor, and/or cable radials projecting away from the building. These additions, while still not reducing the resistance of the system in some instances, will allow the dissipation of the lightning into the earth without damage to the structure. [NFPA-780 Standard for the Installation of Lightning Protection Systems 2008 Edition - Annex B - B.4.3]
Additional precautions must be taken to prevent side-flashes between conductive objects on or in the structure and the lightning protection system. The surge of lightning current through a lightning protection conductor will create a voltage difference between it and any conductive objects that are near it. This voltage difference can be large enough to cause a dangerous side-flash (spark) between the two that can cause significant damage, especially on structures housing flammable or explosive materials. The most effective way to prevent this potential damage is to ensure the electrical continuity between the lightning protection system and any objects susceptible to a side-flash. Effective bonding will allow the voltage potential of the two objects to rise and fall in tandem, thereby eliminating any risk of a side-flash. [NFPA-780 Standard for the Installation of Lightning Protection Systems 2008 Edition - Annex C]
Lightning protection system design
Considerable material is used to make up lightning protection systems, so it is prudent to consider carefully where a rod structure will have the greatest effect. Historical understanding of lightning, from statements made by Ben Franklin, [High-voltage surge eliminator, Roy B. Carpenter, Jr., US patent|5532897. Page 1, Column 1, Line 26-27.] assumed that each device protected a cone of 45 degrees. [Donlon, Tim, " [http://www.buildingconservation.com/articles/lightning/lightn.htm Lightning Protection for Historic Buildings] ". Cathedral Communications Limited, 2001.] This has been found to be unsatisfactory for protecting taller structures, as it is possible for lightning to strike the side of a building. A better technique to determine the effect of a new arrester is called the "rolling sphere technique" and was developed by Dr Tibor Horváth. To understand this requires knowledge of how lightning 'moves'. As the
step leaderof a lightning bolt jumps toward the ground, it steps toward the grounded objects nearest its path. The maximum distance that each step may travel is called the "critical distance" and is proportional to the electrical current. Objects are likely to be struck if they are nearer to the leader than this critical distance. It is standard practice to approximate the sphere's radius as 46 m near the ground. [Installation requirements for lightning protection systems - UL 96A 22.214.171.124.2]
Electricity travels mostly along the path of least resistance, so an object outside the critical distance is unlikely to be struck by the leader if there is a grounded object solidly OR within the critical distance. Noting this, locations that are safe from lightning can be determined by imagining a leader's potential paths as a
spherethat travels from the cloud to the ground. For lightning protection, it suffices to consider all possible spheres as they touch potential strike points. To determine strike points, consider a sphere rolling over the terrain. At each point, we are simulating a potential leader position. Lightning is most likely to strike where the sphere touches the ground. Points that the sphere cannot roll across and touch are safest from lightning. Lightning protectors should be placed where they will prevent the sphere from touching a structure. A weak point in most lightning diversion systems is in transporting the captured discharge from the lightning rod to the ground, though. [Lightning protection installation, US patent|3919956] Lightning rods are typically installed around the perimeter of flat roofs, or along the peaks of sloped roofs at intervals of 6.1 m or 7.6 m, depending on the height of the rod. [Installation requirements for lightning protection systems - UL 96A 8.2.2] When a flat roof has dimensions greater than 15 m by 15 m, additional air terminals will be installed in the middle of the roof at intervals of 15 m or less in a rectangular grid pattern. [Standard for the installation of lightning protection systems 2008 edition - NFPA-780 126.96.36.199]
hould a lightning rod have a point?
This was a controversy as early as the 1700s. In the midst of political confrontation between Britain and its American colonies, British scientists maintained that a lightning rod should have a ball on its end. American scientists maintained that there should be a point. The controversy has not been completely resolved, mostly due to the fact that proper controlled experiments are nearly impossible in such work; in spite of the work of Moore, et al. [described below] most lightning rods seen on buildings have sharp points. Work performed by Moore, et al, in 2000 has helped this issue, finding that moderately rounded or blunt-tipped lightning rods act as marginally better strike receptors. [described below] As a result, round-tipped rods are installed the majority of the time on new systems in the United States.
It is commonly believed, erroneously, that a protector ending in a sharp point at the peak is the best means to conduct the current of a lightning strike to the ground. According to field research, a rod with a rounded or spherical end is better. "Lightning Rod Improvement Studies" [C. B. Moore, William Rison, James Mathis, and Graydon Aulich, " [http://ams.allenpress.com/amsonline/?request=get-abstract&issn=1520-0450&volume=039&issue=05&page=0593 Lightning Rod Improvement Studies] ". Journal of Applied Meteorology: Vol. 39, No. 5, pp. 593–609. Langmuir Laboratory for Atmospheric Research, New Mexico Institute of Mining and Technology, Socorro, New Mexico. April 10, 1999.] by Moore et al say:
: "Calculations of the relative strengths of the electric fields above similarly exposed sharp and blunt rods show that while the fields are much stronger at the tip of a sharp rod prior to any emissions, they decrease more rapidly with distance. As a result, at a few centimeters above the tip of a 20-mm-diameter blunt rod, the strength of the field is greater than over an otherwise similar, sharper rod of the same height. Since the field strength at the tip of a sharpened rod tends to be limited by the easy formation of ions in the surrounding air, the field strengths over blunt rods can be much stronger than those at distances greater than 1 cm over sharper ones.": "The results of this study suggest that moderately blunt metal rods (with tip height to tip radius of curvature ratios of about 680:1) are better lightning strike receptors than sharper rods or very blunt ones."
In addition, the height of the lightning protector relative to the structure to be protected and the Earth itself will have an effect. [US Patent|1266175, Tesla, "Lightning-Protector".] [US Patent|3371144, Griscom, "Transmission-line lightning-proofing structures". Page 25, Column 5. (cf. [...] "the charge on a leader as a function of height above ground" [...] )]
Lightning dissipators have been widely discredited and criticized by lightning researchers over the last 30 years. These terminals (known as "Dissipation Array Systems", and "Charge Transfer Systems") claim to make a
structure"less" attractive to lightning and other charges that flow through the Earth's atmospherearound it. These generally encompass systems and equipment for the preventative protection of objects located on the surface of the earth from the effects of atmospherics. The devices are alleged to deal with the phenomenasuch as electrostatic fields, electromagnetic fields, field transients, static charges, and any other related atmospheric electricityphenomena.
Individual dissipator rods may appear as slightly-blunted metal spikes sticking out in all directions from a metal conductor. [US patent|D478,294 - Haygood, "Lightning dissipation assembly "] These elements are mounted on short metal arms at the top of a
radio antennaor tower, the area most likely to be struck. The dissipation theory states an alteration in the potential difference ( voltage) between the structure and the storm cloudmiles above theoretically reduces but does not eliminate risk of lightning strikes.US patent|6307149, Richard Ralph Zini, et al., Non-contaminating lightning protection system. Claim one and claim ten.] Various manufacturers make these claims. Induced upward lightning strikes occurring on tall structures (effective heights of 300 m or more) can be reduced by altering the shape of the structure.
Evaluations and analysis
controversyover the assortment of operation theories dates back to the 1700s, when Franklin himself stated that his lightning protectors protected buildings by dissipating electric charge. He later retracted the statement, stating that the device's exact mode of operation was something of a mystery at that point. Thus began a 250-year dispute over the dissipation theory versus diversion. Diversion is a misnomer; no modern systems are claimed to divert anything, but rather to intercept the charge that terminates on a structure and carry it to the ground.
The dissipation theory states that a lightning strike to a structure can be prevented by altering the electrical potential between the structure and the thundercloud. This is done by transferring electric charge (such as from the nearby Earth to the sky or vice versa). [John Richard Gumley, US patent|6320119, Lightning air terminals and method of design and application] Transferring electric charge from the Earth to the sky is done by erecting some sort of tower equipped with one or more sharply pointed protectors upon the structure. It is noted that sharply pointed objects will indeed transfer charge to the surrounding atmosphere [Emitter of ions for a lightning rod with a parabolic reflector, Manuel Domingo Varela, US patent|6069314.] [Lightning-protector for electrical conductors, Johathan H. Vail, US patent|357050.] and that a considerable electric current through the tower can be measured when thunderclouds are overhead. It is important to note that unbiased scientific tests have never been performed on any lightning protection system. National laboratories refuse to perform tests, specifically on the charge dissipation method.
The energy in a lightning strike is measured in Joules. The reason that lightning does damage is that this energy is released in a matter of microseconds (typically 30 to 50 microseconds). If the same energy could be released slowly over a period of many seconds or minutes, the current flow would be in milliamperes or a few amperes at most. This is the intent of charge dissipation.
Lightning strikes to a metallic structure can vary from leaving no evidence excepting perhaps a small pit in the metal to the complete destruction of the structure. (Rakov, Page 364Rakov, et al., "Lightning: physics and effects"] ). When there is no evidence, analyzing the strikes is difficult. This means that a strike on an uninstrumented structure must be visually confirmed, and the random behavior of lightning renders such observations difficult. The research situation is improving somewhat, however. [Martin A. Uman, " [http://books.google.com/books?vid=ISBN0486414639&id=9AaG3JnpfcgC Lightning Discharge] ". Courier Dover Publications, 2001. 377 pages. ISBN 0486414639] [Donald R. MacGorman, " [http://books.google.com/books?vid=ISBN0195073371&id=_NbHNj7KJecC The Electrical Nature of Storms] ". Oxford University Press (US), 1998. 432 pages. ISBN 0195073371] [Hans Volland, " [http://books.google.com/books?vid=ISBN0849386470&id=MNPPh7B3WTIC Handbook of Atmospheric Electrodynamics, Volume I] ". CRC Press, 1995. 408 pages. ISBN 0849386470] There are also inventors working on this problem, [Method and apparatus for the artificial triggering of lightning, Douglas A. Palmer, US patent|6012330] [Lightning rocket, Robert E. Betts, US patent|6597559] such as through a
lightning rocket. While controlled experiments may be off in the future, very good data is being obtained through techniques which use radio receivers that watch for the characteristic electrical 'signature' of lightning strikes using fixed directional antennas. [Lightning locating system, Ralph J. Markson et al., US patent|6246367.] [Lightning locating system, Airborne Research Associates, Inc., US patent|5771020.] [System and method of locating lightning strikes, The United States of America as represented by the Administrator of the National Aeronautics and Space Administration, US patent|6420862] [Single station system and method of locating lightning strikes, The United States of America as represented by the United States National Aeronautics and Space Administration, US patent|6552521.] Through accurate timing and triangulation techniques, lightning strikes can be located with great precision, so strikes on specific objects often can be confirmed with confidence.
The introduction of lightning protection systems into standards allowed various manufactures to develop protector systems to a multitude of specifications and there are various lightning rod standards. [NFPA-780 Standard for the Installation of Lightning Protection Systems] [LPI-175 Standard of Practice for the Design - Installation - Inspection of Lightning Protection Systems] [M440.1-1, Electrical Storms and Lightning Protection, Department of Energy] [AFI 32-1065 - Grounding Systems, U. S. Air Force Space Command] [Motorola R-56 Standards and Guidance for Communications Sites] [FAA STD 019e, Lightning and Surge Protection, Grounding, Bonding and Shielding Requirements for Facilities and Electronic Equipment] [IEEE STD 142, Grounding of Industrial and Commercial Power Systems] [IEEE STD 1100, Powering and Grounding Electronic Equipment] [ [http://www.ul.com/lightning/ Lightning Protection Systems] , UL's Lightning Protection program, Underwriters Laboratories] [IEC 62305 Series of lightning protection guidelines] The NFPA's independent third party panel found that "the [Early Streamer Emission] lightning protection technology appears to be technically sound" and that there was an "adequate theoretical basis for the [Early Streamer Emission] air terminal concept and design from a physical viewpoint". (Bryan, 1999 [Bryan, R. G., et al., "Report of the Third-Party Independent Evaluation Panel on the Early Streamer Emission Lightning Protection Technology".] ) The same panel also concluded that "the recommended [NFPA 780 standard] lightning protection system has never been scientifically or technically validated and the Franklin rod air terminals have not been validated in field tests under thunderstorm conditions." In response, the American Geophysical Union concluded that " [t] he Bryan Panel reviewed essentially none of the studies and literature on the effectiveness and scientific basis of traditional lightning protection systems and was erroneous in its conclusion that there was no basis for the Standard." AGU did not attempt to assess the effectiveness of any proposed modifications to traditional systems in its report. [ [http://www.agu.org/focus_group/ASE/NFPAreport.pdf Report of The Committee on Atmospheric And Space Electricity of The American Geophysical Union on The Scientific Basis for Traditional Lightning Protection Systems] ]
No major standards body, such as the NFPA or UL, has currently endorsed a device that can prevent or reduce lightning strikes. The NFPA Standards Council, following a request for a project to address Dissipation Array Systems and Charge Transfer Systems, denied the request to begin forming standards on such technology (though the Council did not foreclose on future standards development after reliable sources demonstrating the validity of the basic technology and science were submitted). [Casey C. Grant, " [http://www.lightningsafetyalliance.com/documents/das_cts.pdf To: Interested Parties] "] Members of the Scientific Committee of the
International Conference on Lightning Protectionhas issued a joint statement stating their opposition to dissipater technology. [Mousa, Abdul M. "Scientists Oppose Early Streamer Air Terminals", 1999.]
Various investigators believe the natural downward lightning strokes to be unpreventable. Since most lightning protectors' ground potentials are elevated, the path distance from the source to the elevated ground point will be shorter, creating a stronger field (measured in volts per unit distance) and that structure will be more prone to ionization and breakdown. [ US Patent|1869661, Bumbraugh, "Lightning protection system and method".] Scientists from the
National Lightning Safety Instituteclaim that these dissipation devices are nothing more than expensive lightning protectors and that they, unlike traditional methods, are not based on "scientifically proven and indisputable technical arguments". [cite web | author=Mousa, Abdul M. | year=1999 | url=http://www.lightningsafety.com/nlsi_lhm/charge_transfer_opp.html | title=Scientists Oppose Early Streamer Air Terminals | format= | work= | publisher= [http://www.lightningsafety.com National Lightning Safety Institute] | accessdate = 2006-09-18 ] William Risonstates that in his opinion the underlying theory of dissipation is "scientific nonsense".cite web | author=Rison, William | year=2001 | url=http://www.lightningsafety.com/nlsi_lhm/magic.pdf | title=There Is No Magic To Lightning Protection: Charge Transfer Systems Do Not Prevent Lightning Strikes | format=pdf | work= | publisher= [http://www.lightningsafety.com National Lightning Safety Institute] | accessdate = 2006-09-18 ] According to these sources, there is no proof that the dissipation arrangement is at all effective. According to opponents of the dissipation technology, the various designs of dissipaters indirectly "eliminate" lightning via the alteration of a building's shape and only have a small effect (either intended or not) because there is no significant reduction to the susceptibility of a structure to the generation of upward lightning strokes.Mousa, Abdul M. "The applicability of Lightning Elimination Devices to Substations and Power Lines". British Columbia Hydro, Burnaby, British Columbia, Canada V3N 4X8.] Some field investigations of dissipaters show that their performance is comparable to conventional terminals and possess no great enhancement of protection. According to these field studies, these devices have not shown that they totally eliminated lightning strikes. [Rison, W., Moore, C.B., and Aulich, G.D., "Lightning air terminals - is shape important?", Electromagnetic Compatibility, 2004. EMC 2004. 2004 InternationalSymposium on Volume 1, 9-13 August 2004 Page(s):300 - 305 vol.1]
Lightning protection for aircraft is provided by mounting devices on the aircraft structure. The protectors are provided with extensions through the
structureof the aircraft's outer surface and within a static discharger. Protection systems for use in aircraft must protect the electronic equipmentwhich is critical to aircraft flight and equipment which is not critical to aircraft flight. Aircraft lightning protection provides an electrical path having a plurality of conductive segments, continuous or discontinuous, that upon exposure to a high voltagefield form an ionizationchannel due to the system's breakdown voltage. Various lightning protection systems must reject the surge currents associated with the lightning strikes. Lightning protection means for aircraft include components which are dielectrics and metallic layers applied to the ordinarily lightning-accessible surfaces of composite structures. Various ground connection means to the layers comprises a section of wire meshfusing the various layers to an attachment connecting the structure which to an adjacent ground structure. Composite-to-metal or composite-to-composite structural joints are protected by making the interface areas conductive for transfer of lightning current.
Some aircraft lightning protection systems use a
shielded cablesystem. These systems carry one or more conductors enclosed by a conductive shield having one end connected to grounding element to provide protection from electrostatic interference. Such systems reduce the electromagnetically induced voltage in a shielded conductor and provides protection from the induced electromagnetic interference of lightning. This network provides a high impedanceand changing to a very-low impedance in response to a momentary voltage surge electromagnetically induced in the shield, thereby establishing a conductive circuit path between the shield and ground. Any surge voltage from lightning drives a shield current through the circuit to provide an electromagnetic field of the opposite direction canceling and reducing the magnitude of the overall electromagnetic field that links the shielded cable.
A lightning protection installation on a
watercraftcomprises a "lightning protector" mounted on the top of the mast or superstructure and a "grounding conductor" in contact with the water. Electrical conductors attach to the protector and run downward to the conductor. For a vessel with a conducting (iron or steel) hull, the grounding conductor is the hull. For a vessel with a non-conducting hull, the grounding conductor may be retractable, part of the hull, or attached to a centerboard.
List of lightning rod patents
Václav Prokop Diviš( 1698- 1765), constructor of the first grounded lightning rod, in Přímětice u Znojmaduring 1750- 1754.
James Otis, Jr., contemporary of Ben Franklin, killed at doorway by lightning in Andover, MAon May 23, 1783.
* Vladimir A. Rakov and Martin A. Uman, " [http://books.google.com/books?vid=ISBN0521583276&id=NviMsvVOHJ4C Lightning: physics and effects] ". Cambridge University Press, 2003. 698 pages. ISBN 0521583276
* J. L. Bryan, R. G. Biermann and G. A. Erickson, "Report of the Third-Party Independent Evaluation Panel on the Early Streamer Emission Lightning Protection Technology". National Fire Protection Association, Quincy, Mass., 1999.
* Kithil, Rich. "More on lightning rods...", Lightning Safety Home Page, Message #402.
May 8, 2000. (Response to C. B. Moore) Originally at: http://www.thomson.ece.ufl.edu/lightning/Moore%20on%20air%20terminals.htm
* M. A. Uman and V. A. Rakov " [http://www.lightningsafety.com/nlsi_lhm/Uman_Rakov.pdf Critical Review of Nonconventional Approaches to Lightning Protection] ", Bulletin of the American Meteorological Society, December 2002.
* Mousa, Abdul M. " [http://www.lightningsafetyalliance.com/documents/lightning_war.pdf War of the Lightning Rods] ", Electricity Today, 2004.
* Zipse, Donald. " [http://www.powerquality.com/mag/power_prevent_lightning_strikes/index.html Prevent Lightning Strikes with Charge Transfer Systems] ", Power Quality, November 2001
* Zipse, Donald. "Lightning protection methods: An update and a discredited system vindicated", IEEE Trans. on Industry Applications, 37, 407-414, 2001.
* Carpenter, Jr., Roy B. " [http://lecglobal.com/info/tech-papers/preventing-direct-lightning-strikes.pdf Preventing Direct Strikes] ". August 2005.
*" [http://www.usatoday.com/weather/resources/basics/2000-05-15-lightn-rod-tests.htm Researchers find that blunt lightning rods work best] ".
USA Today. (06/10/2002)
Federal Aviation Administration, " [http://ntl.bts.gov/card_view.cfm?docid=22344 FAA-STD-019d, Lightning and surge protection, grounding, bonding and shielding requirements for facilities and electronic equipment] ". [http://ntl.bts.gov/ National Transportation Library] , 2002-08-09.
* Kithil, Richard, " [http://www.lightningsafety.com/nlsi_lhm/lightning_rod_recent.html Lightning Rods: Recent Investigations] ". [http://www.lightningsafety.com/ National Lightning Safety Institute] ,
September 26, 2005.
* Kithil, Richard, " [http://www.lightningsafety.com/nlsi_lhm/InstallRods.html Should Lightning Rods be Installed?] ". National Lightning Safety Institute,
September 26, 2005.
* Kithil, Richard, " [http://www.lightningsafety.com/nlsi_lhm/lpts.html Fundamentals of Lightning Protection] ". National Lightning Safety Institute,
September 26, 2005.
* Nailen, Richard L., " [http://www.findarticles.com/p/articles/mi_qa3726/is_200102/ai_n8940245 Lightning controversy goes on] ", The Electrical Apparatus, February 2001.
* [http://www.lightningsafetyalliance.com/education.html Lightning Safety Alliance education] page
* Richard Owen, Wm S Orr, John Radford Young, Alexander Jardine, Robert Gordon Latham, Edward Smith, William Sweetland Dallas, "Orr's Circle of the Sciences", [http://books.google.com/books?id=Xcg4AAAAMAAJ&pg=PA232 Atmospheric Electricity—Theory of Lightning-rods] W.S. Orr 1855.
Wikimedia Foundation. 2010.
Look at other dictionaries:
Lightning rod — Lightning Light ning (l[imac]t n[i^]ng), n. [For lightening, fr. lighten to flash.] 1. A discharge of atmospheric electricity, accompanied by a vivid flash of light, commonly from one cloud to another, sometimes from a cloud to the earth. The… … The Collaborative International Dictionary of English
lightning rod — lightning rods 1) N COUNT A lightning rod is the same as a lightning conductor. [AM] 2) PHRASE: PHR n If you say that someone is a lightning rod for something, you mean that they attract that thing to themselves. [AM] He is a lightning rod for… … English dictionary
lightning rod — lightning .rod n AmE 1.) a ↑lightning conductor 2.) someone or something who gets most of the criticism, blame, or public attention when there is a problem, although they may not be responsible for it be a lightning rod for sth ▪ The senator has… … Dictionary of contemporary English
lightning rod — lightning ,rod noun count AMERICAN 1. ) a metal bar fixed to a building that protects it from LIGHTNING 2. ) someone who attracts a lot of criticism, sometimes as a way of protecting someone else: The outspoken chief inspector serves as a… … Usage of the words and phrases in modern English
lightning rod — Someone or something that attracts a lot of negative comment, often diverting attention from other problems, is a lightning rod … The small dictionary of idiomes
lightning rod — ☆ lightning rod n. 1. a tall metal pole placed high on a structure, as a building or tower, and attached to a ground so as to attract lightning and protect the structure from damage 2. a person or thing that attracts controversy, strong feelings … English World dictionary
lightning rod — 1. a rodlike conductor installed to divert lightning away from a structure by providing a direct path to the ground. 2. a person or thing that attracts and absorbs powerful and esp. negative or hostile feelings, opinions, etc., thereby diverting… … Universalium
lightning rod — noun Date: 1773 1. a grounded metallic rod set up on a structure (as a building) to protect it from lightning 2. one that serves to divert attack from another 3. one that is a frequent target of criticism or focus of controversy < she has become… … New Collegiate Dictionary
lightning rod — /ˈlaɪtnɪŋ rɒd/ (say luytning rod) noun 1. → lightning conductor. 2. someone or something which attracts heated debate: an agreement which is a lightning rod for both sides of politics … Australian English dictionary
lightning rod — n. someone, something, or an issue that is certain to draw criticism. □ Why write such a boastful introduction to your book? It will just be a lightning rod for criticism. □ We didn’t hire him for the part since his opinionated comments make him… … Dictionary of American slang and colloquial expressions