Neptune Bank Power Station
Neptune Bank Power Station Country England Location Wallsend Coordinates Coordinates: Status Demolished Construction began 1900 Commission date 18 June 1901 Decommission date 1915 Operator(s) Newcastle upon Tyne Electric Supply Company Power station information Primary fuel Coal Generation units Four 700 kW (1901)
Two 1,500 kW (1902)
Turbine manufacturer(s) Parsons Power generation information Installed capacity 2,800 kW (1901)
3,000 kW (1902)
grid reference NZ299655
Neptune Bank Power Station was a coal-fired power station situated on the River Tyne at Wallsend near Newcastle upon Tyne. Commissioned in 1901 by the Newcastle upon Tyne Electric Supply Company, the station was the first in the world to provide electricity for purposes other than domestic and street lighting. It was also the first in the world to generate electricity using three-phase electrical power distribution at a voltage of 5,500 Volts.
The station had an initial generating capacity of 2,800 kW, which was increased to 3,000 kW a year after the station opened, with the introduction of two 1,500 kW Parsons turbo alternators, the largest ever built at that time. The station closed in 1915, following the completion of an extension to Carville Power Station and the opening of Dunston Power Station.
At the beginning of the twentieth century, the use of electricity for general purposes began to be considered, and the Newcastle upon Tyne Electric Supply Company (NESCo) realised the potential it offered for development. In June 1899, the Walker and Wallsend Union Gas Company (WWUGC) acquired Parliamentary powers for the supply of electricity to the area around Wallsend. In January 1900 they erected Neptune Bank power station near the North Eastern Railway's (NER) North Tyneside Loop, midway between Wallsend and Walker. In October 1900, NESCo acquired the entire power station from the WWUGC, with the exception of the cables and sub-station machinery installed for the purpose of supplying the works in the area in which the WWUGC had obtained Parliamentary powers. the WWUGC continued to buy electricity in bulk from NESCo.
The station was officially opened on 18 June 1901 by Lord Kelvin. At the opening he said:
"We have seen at work what many have not seen before - a system realised in which a central station generates power by steam engines and delivers electricity to consumers at distances varying, I think, from a quarter of a mile to over three and a half miles... A larger station is in prospect, larger work is contemplated. This admirable but comparatively small station at Neptune Bank makes a splendid beginning... What I am seeing today is the dream of my life realised. I do not know the limits of electricity, but it will go beyond anything we can conceive of today."
The station was the first power station to generate electricity for industrial purposes, rather than just for domestic and street lighting, and this led to a rapid expansion of NESCo.
NESCo laid high-tension cables from the power station to various substations in Newcastle upon Tyne. The company changed their system of supply, from 2,000 Volt (V) single phase alternating current which had been used to distribute power from their Pandon Dene Power Station, to three phase current at 5,500 V. This made NESCo the first statutory authority to supply in such a way. The scientific journal, The Electrician congradutalted NESCo in June 1901, stating that "not merely electric power supply on Tyneside was formally inaugurated last Tuesday, but the era of electric power utilisation all over the kingdom."
A year after the station came into operation, NESCo's original power station at Pandon Dene was closed and converted into a substation. The Pandon Dene station had originally supplied Newcastle city centre with electricity, but the new Neptune Bank station took over this supply, transmitting using high voltage cables laid in ducts, rendering the older station obsolete.
Design and specification
The station's buildings were built from corrugated iron, and the boiler house adjoined the engine room on its south facing side. Each of these two buildings measured 100 feet (30 m) by 52 feet (16 m). To the north east of the main station buildings lay the station's cooling pond, where the station's circulating water was cooled by means of spray nozzles, capable of cooling 4,000,000 pounds of water per hour. This cooling system was adopted as it was cheaper than pumping water up from the nearby River Tyne which was 60 feet (18 m) below the level of the station. The station was also equipped with a testing pond, capable of absorbing up to 1,500 kW.
Coal was delivered to the station via the NER's North Tyneside Loop. An electric locomotive was used to convey the coal from the railway to the boiler house. The station's boiler house was equipped with four batteries of two Babcock & Wilcox boilers. Each boiler had a capacity of 1,000 horsepower and a working pressure of 200 psi. Each was fitted with superheaters and mechanical stokers and had a heating surface of 4,020 square feet, with a superheat of 100 - 120 degrees Farenheit. Each could evaporate 14,000 pounds of water per hour. Ash waste from the boilers was discharged into trucks.
The station initially generated electricity using four 700 kilowatt (kW) alternators, each driven by a slow-speed triple expansion marine type reciprocating engine, built by Wigham Richardson & Co. and the Wallsend Slipway & Engineering Company. The station was the first in the world to generate electricity using three-phase electrical power distribution at a voltage of 5,500 V, and the first to generate direct current at different voltages. After the opening of Carville Power Station in 1904, the voltage of transmission was raised to 6,000 V.
In 1902, two 1,500-kW Parsons steam turbine driven turbo-alternators were added to the initial equipment at the station. At the time, these were the largest three-phase steam turbine driven alternators in the world, as well as being the first of the barrel type rotary design. Results gained from the turbines influenced the Cunard Steamship Company to install steam turbines on the Mauretania. The turbines drove 6,000 V three-phase alternators, supplying current to motor-generators and transformers in the substations attached to the distribution network. The motor-generators in the substations provided DC from the supplied AC and the transformers stepped-down the 6,000 V supply to 200 V for lighting use and 400 V for industrial use.
By 1904, there were a total of nine different generating sets operating at the power station. Sets No. 1 and 2 were DC generators driven by 300 HP two-crank compound engines running at 380 RPM, power from which supplied DC network in Wallsend and Walker. Set No. 3 was a 50 kW set used for exciting purposes only. Sets No. 4 and 5 were used as balancers and motor generators and had a combined capacity of 150 kW. Sets No. 6, 7, 8 and 9 were each driven by 1,400 HP engines and in turn each drove a 750 kW alternator. The two Parsons sets worked alongside these.
Coal was delivered to Neptune Bank from the Riverside Branch of the North Eastern Railway at Tyne Pontoons signal box, about halfway between Walker and Carville stations. It was taken to the station's railway sidings using a small electric locomotive and unloaded in front of the boiler house. It was then hand-loaded into automatic stokers which fired the boilers. Removal of ash from the boilers was performed by machine.The station was badly located for sources of cooling and boiler water - it was some 60 feet above the level of the nearby River Tyne, which was also 200 feet away. The concept of a cooling tower had not yet been invented and a large but inefficient brick-built cooling pond was used.
Following Neptune Bank's commissioning there was a rapid increase in the demand for electricity, which couldn't be met by the station, and so in 1904 NESCo commissioned Carville Power Station. Fitted entirely with steam turbine generating equipment, Carville quickly superseded Neptune Bank. Neptune Bank power station was largely out of use by 1909 after the extension of the Carville station, along with the opening of Dunston Power Station. It was decommissioned in 1915 and the site was used by NESCo as a storage facility.
- ^ a b c d e f g North-Eastern Electric Supply Company Limited 1889-1948. Newcastle upon Tyne: T.M Grierson Ltd. March 1948.
- ^ a b c d e "Full text of "The Mining engineer"". archive.org. http://www.archive.org/stream/miningengineer07goog/miningengineer07goog_djvu.txt. Retrieved 9 August 2011.
- ^ "We were all off-grid once". off-grid. http://www.off-grid.net/book-extracts-from-how-to-live-off-grid-by-nick-rosen/extract-2-we-were-all-off-grid-once/. Retrieved 2008-09-03.
- ^ "North Eastern Electricity Board". The National Archives. http://www.nationalarchives.gov.uk/a2a/records.aspx?cat=183-dueb&cid=0. Retrieved 2008-09-03.
- ^ a b Mr Alan Shaw (29 September 2005). "Kelvin to Weir, and on to GB SYS 2005". Royal Society of Edinburgh. http://www.royalsoced.org.uk/enquiries/energy/evidence/ShawA1.pdf.
- ^ a b c d e Parke Hughes, Thomas (1993). Networks of Power. JHU Press. p. 456. ISBN 0801846145. http://books.google.co.uk/books?id=g07Q9M4agp4C. Retrieved 2009-02-08.
- ^ a b c National civic federation Commission on public ownership and operation, ed. Municipal and Private Operation of Public Utilities. 2. National civic federation. p. 301. http://www.archive.org/stream/p2municipalpriva02natiuoft/p2municipalpriva02natiuoft_djvu.txt. Retrieved 2009-02-02.
- ^ "Full text of "Transactions of the North-east coast institution of engineers and shipbuilders .."". www.archive.org. http://www.archive.org/stream/transactionsnor10shipgoog/transactionsnor10shipgoog_djvu.txt. Retrieved 22 March 2011.
- ^ a b "Survey of Belford 1995". North Northumberland Online. http://www.nnouk.com/survey/survey-utilities.shtml. Retrieved 2008-09-03.
Deptford East Power Station
Largest Power Station in the UK
Carville A Power Station
Electricity generation in North East England Generating
sitesActiveBiomass Energy Centre · Lynemouth (co-fires) · Wilton 10Proposed/FutureBEI-Teesside · Billingham · North Blyth · Teesport · Tyne REPActiveLynemouth · WiltonClosedBerwick upon Tweed · Blyth · Carville · Chopwell Colliery · Close · Consett · Darlington · Derwenthaugh Coke Works · Dunston · Forth Banks · Hebburn · Horden Colliery · Lemington · Mainsforth Colliery · Manors · Morrison Busty Colliery · Neptune Bank · Newburn Steelworks · North Tees · Ouston Colliery · Pandon Dene · Philadelphia · South Shore Road · South Shields · Stella · Sunderland · Vane Tempest Colliery · WhinfieldProposed/FutureEston Grange (Gasification)Refused/ShelvedBlyth Clean Coal · KepierActiveSeal Sands · Teesside · WiltonProposed/FutureConocoPhillips Teesside · Thor CogenerationRefusedNewburnActiveClosedActiveRefusedActiveWiltonActiveTeesside · Path Head landfillClosedFutureNorth Eastern Energy Recovery Centre · Wilton 11RefusedActiveBlyth Harbour · Blyth Offshore · Broom Hill · Great Eppleton · Hare Hill · High Sharpley · High Volts · Holmside Hall · Kirkheaton · Langley Park · Tow Law · Trimdon Grange · Walkway · West DurhamFutureBlyth Harbour (repowering) · Butterwick Moor · Great Eppleton (repowering) · Haswell Moor · Kiln Pit Hill · Lynemouth · Royal Oak · TeessideProposedBarmoor South · Green Rigg · Kielder · Moorsyde · Ray Hill · South Sharpley · Steadings · Teeswind North · The Isles · Todd Hill · West Ancroft · Wingates
and personnelA. Reyrolle & Company · C. A. Parsons and Company · CE Electric UK · Charles Algernon Parsons · Charles Hesterman Merz · Clarke Chapman · John Theodore Merz · L J Couves & Partners · Merz & McLellan · NaREC · Newcastle and District Electric Lighting Company · North Eastern Electric Supply Company · Northern Electric · Northern Engineering Industries · Pre-nationalisation North East electric power companies
Wikimedia Foundation. 2010.
Look at other dictionaries:
North Tees Power Station — North Tees A, B C Power Stations North Tees C Power Station in the 1980s … Wikipedia
Deptford Power Station — Deptford West Power Station Viewed from the east in July 1973 … Wikipedia
Dunston Power Station — Dunston B Power Station Viewed from southwest … Wikipedia
Consett Power Station — Consett Power Station … Wikipedia
Darlington Power Station — For the nuclear power plant in Canada, see Darlington Nuclear Generating Station. Darlington Power Station Darlington railway station with the power station in the background … Wikipedia
Manors Power Station — in 2009 Official name Manors Power Station Country England Location … Wikipedia
Close Power Station — Country England Location Tyne and Wear, North East England Coordinates … Wikipedia
List of power stations in England — Note that the DBERR maintains a comprehensive list of UK power stations [http://www.berr.gov.uk/energy/statistics/source/electricity/page18527.html here] . This is a list of electricity generating power stations in England, sorted by type and… … Wikipedia
Champlain Hudson Power Express — The Champlain Hudson Power Express (CHPE) is a high voltage direct current (HVDC) submarine power cable project linking the Montreal area to the New York City suburb of Yonkers. If approved, the line is expected to be commissioned in 2015. The… … Wikipedia
North Eastern Electric Supply Company — Former type Private Industry Electricity supply Fate Nationalised Successor North Eastern Electricity Board … Wikipedia